Application of Energy Consumption Management System in Guli Fire Station of Changshu
Contributed by Ankerui Electric Co., Ltd. 2019/12/23 9:04:02
0 Popularity: 4
- Keywords: Energy consumption monitoring system ACREL-5000
- Abstract: With the improvement of social living standards and the prosperity of the economy, people's demand for energy has gradually increased, resulting in an increasingly serious energy crisis. How to understand, analyze and control the school's energy consumption in real time has become an urgent problem to be solved. Traditional energy consumption intelligence is performed on a monthly / quarterly / yearly cycle. However, schools are daily and hourly, and energy consumption occurs daily and hourly. This article introduces the Guli Fire Station project in Changshu. It uses Ankerui intelligent power meters to collect various electrical parameters at the power distribution site. The system adopts the on-site networking method. After networking, the Acrel-5000 energy consumption monitoring system is used to achieve various Monitoring and management of power consumption in distribution circuits.
Abstract : With the improvement of social living standards and the prosperity of the economy, people's demand for energy has gradually increased, resulting in an increasingly serious energy crisis. How to understand, analyze and control the school's energy consumption in real time has become an urgent problem to be solved. Traditional energy consumption intelligence is performed on a monthly / quarterly / yearly cycle. However, schools are daily and hourly, and energy consumption occurs daily and hourly. This article introduces the Guli Fire Station project in Changshu. It uses Ankerui intelligent power meters to collect various electrical parameters at the power distribution site. The system adopts the on-site networking method. After networking, the Acrel-5000 energy consumption monitoring system is used to achieve various Monitoring and management of power consumption in distribution circuits.
Keywords: fire station; energy consumption monitoring system; ACREL-5000
With the deepening of energy conservation, the scientific management methods of energy utilization are becoming more diverse. The energy consumption management system can monitor the detailed use of various energy sources in the school in real time, find weaknesses in energy consumption for public buildings, promote the improvement of school management and reduce operating costs, and provide an intuitive and scientific basis for energy conservation and consumption reduction. As an efficient management tool and emerging management means, energy consumption management systems have been applied in large public buildings, hospitals and other fields. Changshu Guli Fire Station Acrel-5000 energy consumption management system reduces energy consumption and improves profit through energy collection and management.
2 Design basis
GBT23331-2009 "Energy Management System Requirements"
GB-50052-2009 "Code for Design of Power Supply and Distribution System"
National and industry standards for energy consumption measurement devices
DL / T 645-1997 Multi-function Energy Meter Communication Protocol
DL / T 645-2007 Multifunctional Energy Meter Communication Protocol
CJ / T 188-2004 Technical Conditions for Data Transmission of Household Meters
3 Project Overview
Changshu Guli Fire Station mainly monitors multi-function meters on the floor. There are a total of 16 PZ and DS series meters manufactured by Ankerui, including 7 PZ80L-E4 and 9 DTSD1352, which are connected to the system by two buses.
4 System architecture
According to the actual situation of the public construction site, the Acrel-Acrel-5000 energy analysis management system uses a shielded twisted pair to directly connect to the background energy gateway and then upload the data to the monitoring host through the TCP / IP network. The details are shown in the following figure:
The system mainly uses a layered distributed computer network structure, as shown in the system structure diagram: station control management layer, network communication layer and field equipment layer. The meters in the entire building are distributed in the power distribution room and floors. All the meters are laid to the monitoring center through 485 shielded twisted-pair wires, and are collected and managed by the energy gateway to the system host.
5 System software modules
Main interface of comprehensive energy consumption
The main page displays the building's architectural picture, basic building information, the monthly electricity pie chart of the building, and various energy consumption. According to the selected building, load its building picture, you can choose the time to view the energy consumption of the building, select the building or the time to automatically refresh, the default is the day.
The system can count the energy usage of each branch road day by day, week by week, month by month, quarter by quarter, and year by year. The system can view the energy consumption trend of each branch, and can make inquiries based on the existing date or custom time, and can display the total energy consumption of the branch in a chart form.
Breakdown of energy consumption by item
The system can perform energy consumption statistics and display according to items. Among them, the year-on-year analysis chart of daily energy consumption shows the energy consumption histograms of different sub-items for the day and yesterday (the blue bar represents today and the green bar represents yesterday); the energy pie chart shows the energy consumption of each sub-item in the past 31 days. The stacked graph shows the energy consumption trend of each sub-item in the past 31 days. The sub-item energy ranking chart shows the top 10 branches of the energy consumption value corresponding to the selected sub-item.
Itemized energy consumption report
The system can count daily, weekly, monthly, quarterly, and yearly energy consumption of each sub-item within a certain period of time. You can view the energy consumption trend of each branch in the sub-items, you can query based on the existing date or custom time, and the statistical data can be exported to Excel.
Year-on-year analysis of energy consumption
The system can analyze the energy consumption of each major energy-consuming equipment from the same period of last year and the value of the previous month on a year-on-year basis, check the energy-saving effect, perform energy-saving performance assessment, and revise energy-saving targets based on the analysis results. Statistics on the monthly energy consumption of each branch road in the current year and the same period last year;
Energy data check
The system can calculate the energy difference between each loop and the lower branch in a certain period of time. When it exceeds a certain percentage, it will be prominently displayed (red area) to ensure the integrity and accuracy of the measurement system.
Configure the basic information of the building in accordance with the relevant technical specifications, such as: building functions, building area, air-conditioning area, building address, etc., where the building area and other information will be analyzed by energy consumption per unit area;
Configure basic information such as the type, model, and manufacturer of the meter used in the project, and add the monitoring parameter information that the meter can provide. The configuration here affects energy consumption statistics, energy consumption statistics by period, and parameter query functions;
Configure all measuring instruments used in the project, and save the address, transformation ratio, corresponding collector, code, name of the monitoring circuit and other information of the measuring instrument;
The information such as the meter, proportion, and calculation method involved in configuring the energy consumption statistics of each item can be flexibly configured according to the project situation. The configuration information here will affect the functions in the energy consumption analysis modules of each category. ;
Configure the energy consumption metering, calculation method, proportion and department energy consumption plan for each department. After completing this configuration, the department energy analysis function module will be enabled;
Configure the meter, calculation method, and proportion corresponding to an energy-consuming area in the building. After completing this configuration, the regional energy analysis function module will be enabled.
Based on the analysis of the energy consumption operation effect of school buildings, a typical energy consumption analysis model is established and unified analysis.
Establish a building energy consumption measurement system: For the publicly-used power structure, monitor to the distribution room level, and accurately calculate the incoming and outgoing loops. The principle of electrical energy conservation must be met, that is, the incoming electric energy is the sum of outgoing electric energy (error rate is 3%). about).
The collected data is stored and formed into a visual chart: the system collects the data and stores it in a database, the system can meet the report query and export, and the system can display the energy consumption trend in the form of histograms, etc., to give customers a better experience.
Diagnosing high energy consumption points: Managers can collect data through the system, and analyze the year-on-year and quarter-on-quarter comparisons of each circuit. A one-stage analysis can find high energy consumption points.
Improve management and operation mode through energy consumption analysis: For high energy consumption points, positively improve management operations, such as: notifying various teams to turn off lights and shutting down machines during off-hours, and include them in performance appraisal; during the work period, the power load is relatively large. The circuit can shift peaks and reduce excessive load at the same time; the energy consumption data can reduce the company's operating costs and increase profits.
The energy consumption system of Changshu Guli Fire Station is designed for the problem of energy consumption in schools under the background of increasing energy problems and rising energy prices. After the construction of the energy consumption management system, it will not only reduce the workload of the staff and provide work efficiency, but also the intuitive statistical analysis results can more effectively help the building managers to make correct analysis based on the energy consumption situation and to develop in the future. Making the right decisions is of great significance to promoting and driving energy conservation and achieving energy conservation and emission reduction goals.
About the Author:
Zhang Xiaoli, female, bachelor Ankerui Electric Co., Ltd., main research direction is smart grid power supply
Scan QR code on your phone to share this page
Download and install Gongkong APP